PetroChina Company Limited, Dushanzi, China
PetroChina Company Limited is China's largest oil and gas producer and distributor, and plays a dominant role in the country's oil and gas industry. Dushanzi Petrochemicals, a primary subsidiary of PetroChina, operates China's largest refinery and petrochemical complex. Operational since 2009, it can process 10 million tons of crude oil and produce 1.2 million tons of ethylene per year as well as a range of fuels and other refinery products. In 2007, Yokoshin Software Engineering (WuXi) Co., Ltd., a Yokogawa subsidiary, successfully installed the distributed control systems (DCS) for this megasize complex.
Dushanzi Petrochemicals also has refinery, polyethylene, utility, and other facilities at this complex that date back to the 1990s. Some of these relied on older control systems that were experiencing steadily rising failure rates and issues with the availability of spare parts. In consideration of Yokoshin Software Engineering's success in implementing the systems for the refinery & petrochemical complex megaproject and Yokogawa's rich system migration experience, Dushanzi Petrochemicals awarded Yokogawa a contract in November 2010 that included the revamp of the legacy Honeywell TDC3000 DCS at the complex's polyethylene plant. This was successfully completed in October 2011 after a 50-day shutdown period and site acceptance testing (SAT). With the conclusion of the system migration work at the Dushanzi complex, most of its DCS systems are now from Yokogawa, significantly reducing its maintenance costs.
About This Project
The plant's TDC3000 system had eight DCS controllers, one safety controller, ten HMI/ENG stations, one application module, and one history module. With Triconex responsible for upgrading their legacy safety system, the scope of Yokogawa's work was limited to the replacement of the TDC3000 system with a CENTUM DCS. There was no manufacturing execution system (MES) at the plant.
A typical TDC3000 system layout
Based on documents about the polyethylene production process (a BP gas-phase technology) and discussions with the customer's engineers, Yokogawa understood it would be a demanding project, with many complex sequence controls, calculations, interlocks, and loops in the existing DCS.
The Challenges and the Solutions
Throughout the revamp, which included the challenging creation of function design specifications (FDS) as well as factory acceptance testing (FAT) and SAT, Yokogawa took a team approach and worked closely with the customer. With the strong support of Dushanzi's management and employees, this work was completed on time.
(1) How to create an FDS for a revamp project
Creating an FDS is always our first aim during a plant revamp project. As the customer required us to realize all of the TDC3000 system's functions, its system database was the focus of our investigation. The existing plant had been completed in 1995 and expanded in 2002, so some of the function definitions could be found in the TDC3000 database, but it was not possible to identify the corresponding functions in the production process. Yokogawa's engineers checked every item in the database and worked with the customer to confirm a list of objects for the database conversion.
The TDC3000 database could only show Yokogawa's engineers what kind of function blocks had been implemented. Not enough information was available to understand the production process or the operation procedures at the polyethylene plant, both of which were of key importance in migrating to the new system. The Yokogawa personnel set about trying to interpret the database by referring to the original documents that had been released in 1995 by the licenser of the polyethylene production process and Honeywell. In addition, Yokogawa's global engineering team assisted by providing analytical insights and tools that aided in the conversion of database control language and the visualization of logic functions.
The customer's instrumentation and operations experts were very knowledgeable about the TDC3000 system and the polyethylene plant, so Yokogawa's engineers could clarify all unclear points in discussion with them and explain how Yokogawa would implement and realize existing functions on the Yokogawa CENTUM system, particularly those where changes were necessitated by architectural differences between the two systems.
As the customer was involved throughout the FDS creation process, Yokogawa could quickly complete this work and customer approval went smoothly. The following formula expresses Yokogawa's best practice in creating an FDS for a migration project:
FDS = existing database + original documents + knowledge of customer's experts
(2) Three factory acceptance tests (FAT)
As part of this project, Yokogawa conducted a pre-FAT, an official FAT, and a post-FAT to mitigate potential risks in the SAT phase. More than 13 experts were dispatched from the customer's process, instrumentation, and operation departments for the official four-week FAT. Working with Yokogawa's engineers, five teams were mobilized respectively to check all items in sequences, complex loops, complex calculations, logic, and graphics. The customer experts played a very important role by providing necessary clarifications to Yokogawa personnel on a number of points and giving many constructive suggestions on modifications.
Official FAT at Yokoshin Software Engineering
The plant was shut down for about 50 days, giving Yokogawa enough time to do a cold cut-over to the new DCS. All Honeywell terminal boards were dismantled, leaving nothing but Yokogawa system hardware.
The following approach was taken to optimize the SAT process:
- Digitally Enhanced (DE) protocol instruments were changed to HART or analog mode to reduce workload.
- To ensure the integrity of the existing TDC3000 database, rather than immediately making changes to it to correct a problem reported by the customer, we investigated carefully to find the actual cause. For example, during the SAT, the customer requested an increase in the valve delay time to resolve a transient alarm. However, a detailed investigation found that the positions of two valve switches had been reversed.
- To prevent mistakes, a policy requiring multiple approvals for function modifications requested by customer engineers was adopted.A team of over 30 people from Dushanzi, Yokogawa, and subcontractors assisted with the system installation and cut-over.
Pre-revamp CCR with legacy Honeywell TDC3000 system
Post-revamp CCR with CENTUM system
Zhaoshan Sun, Chief Instrument Manager, said, "In 2007, Yokoshin Software Engineering performed flawlessly on the refinery & petrochemical complex megaproject. Their strict, careful, and effective approach in their work ensured a successful startup and stable operation of the DCS. The Dushanzi project strengthened Yokoshin's reputation in China's petrochemical industry. When we were considering a revamp of the legacy system at our polyethylene plant, we chose Yokoshin as our migration partner based on our assessment of their capabilities and strengths."
Mr. Sun went on to say, "Yokoshin's project manager and engineers worked closely with us to understand every technical problem and control the project schedule. The experts from Yokogawa headquarters also gave us timely support by sharing TDC3000 knowhow. To clarify details of the sequence program and calculation formulas, their engineers often worked late with us. Their rigorous, serious, and responsible approach not only helped overcome all difficult problems, but also made a good impression. The process unit has been running well and is problem-free since the start-up, and we wish to express our heartfelt thanks for this to Yokoshin!"
Key Project Achievements
- Replacement of all TDC3000 system functions (IO points: 5,000)
- Smooth and safe cutover to CENTUM CS3000 system
- 100% production performance
Yokogawa bedient de markt voor bulkchemicaliën wereldwijd en is de erkende leider in deze markt. Met producten, oplossingen en industrie-expertise begrijpt Yokogawa uw markt- en productiebehoeften en werkt met u samen om een betrouwbare en kosteneffectieve oplossing te bieden gedurende de gehele levenscyclus van uw fabriek.
Chemische fabrieken zijn afhankelijk van continu- en batch-productieprocessen die elk verschillende eisen stellen aan een besturingssysteem. Een continu proces vereist een robuust en stabiel besturingssysteem dat niet faalt en de productielijn doet stilvallen. Bij een batchproces ligt de nadruk ligt op een besturingssysteem dat een grote flexibiliteit biedt bij het aanpassen van o.a. formules en procedures. Beide soorten systemen moeten worden beheerd naar aanleiding van de productiegeschiedenis rond de kwaliteit van het product, en in staat zijn om niet-routinematige werkzaamheden uit te voeren. Met een uitgebreide productportfolio, ervaren systeemingenieurs en wereldwijde verkoop- en servicenetwerk heeft Yokogawa een oplossing voor elk fabrieksproces.
De behoeften van petrochemische bedrijven zijn zeer divers. Om voorop te blijven lopen in de huidige, sterk concurrerende markt, streven producenten naar verbetering van kwaliteit en productiviteit. Yokogawa biedt op maat gemaakte oplossingen voor deze behoeften op basis van haar lange en brede ervaring op dit gebied.
Gerelateerde producten & oplossingen
Gedistribueerd besturingssysteem (DCS)
De DCS maakt automatisering en controle van industriële processen en verbeterde bedrijfsprestaties mogelijk. Meer dan 10.000 fabrieken vertrouwen op Yokogawa DCS om hun productiedoelen te bereiken.