Hafeezur Rahman1 Ng Kim Fatt1 Hideyuki Sakamoto1
In July 2010, Yokogawa became the first vendor to offer Field Wireless solutions based on the ISA100.11a standard, by releasing the YFGW710 field wireless integrated gateway, and the wireless pressure and temperature transmitters. In 2012, as field wireless becomes more popular, a high performance gateway that can support a large number of devices was required. Therefore in July this year, Yokogawa expanded the wireless solution lineup with the enhanced YFGW410 Field Wireless Management Station and its supporting devices. On the other hand, as the usage of field wireless solutions for plant control and monitoring grows, there is a pressing need for the plant asset management software–Plant Resource Manager (PRM)– and the device configuration system–FieldMate– to support the management and maintenance of field wireless devices. This paper describes the new functions that have been added to PRM to fulfill this requirement.
|Figure 1 PRM configuration for managing devices|
As compared to Distributed Control Systems (DCS) such as CENTUM VP that monitors the operations of the overall plant, PRM1 2 is a type of Plant Asset Management3 (PAM) software package that primarily focuses on the maintenance of devices and instruments.
PRM is equipped with the functions that are expected of an online PAM system. Some of the main functions are as follows:
PRM fully supports communication standards such as HART, FOUNDATION fieldbus™ (FF-H1), PROFIBUS, and FDT/DTM (Field Device Tool/Device Type Manager4) interface standards. On top of that, it is equipped with a plant hierarchy display function that is based on the IEC61512/ ISA-88 standard. However, with the advent of the ISA100.11a standard, PRM had to be enhanced to support this standard too. The following sections describe the details of the enhanced PRM modules, and the roles they play in realizing ISA10 0.11a support.
Figure 1 gives a high level view of the configuration by which PRM communicates and manages devices. The blocks in purple indicate the PRM systems while the remaining blocks indicate other systems and devices.
PRM Client is a human machine interface (HMI) application that is used to manage all assets according to the ISA-88 plant hierarchy model. Higher hierarchy levels of the plant such as Site or Area are used to logically compile physical devices and instruments. Many of the functions mentioned earlier are provided by this application. On top of that, the following functions are also provided.
PRM Server and the Field Communication Server is responsible for functions such as master data storage, plug and play device registration, data acquisition, device status scanning, and online device communication.
PRM Server is the back-end system that supports PRM Client. Some of the main functions are as follows:
Field Communication Server
The Field Communication Server (FBCOM) enables PRM to communicate online with field devices. The devices connected to the various Yokogawa control systems (such as FCS, FCN, SCS) are able to maximize PRM performance by using their own proprietary communication method. FBCOM is also equipped with an interface that adopts the Device Type Manager (DTM) technology, which is the industry standard. This enables PRM to communicate with different field devices that conform to different standards, especially for PROFIBUS and ISA100.11a devices such as bus converters and communication gateways. Communication is possible as long as the corresponding CommDTMs or GatewayDTMs are available. The characteristics of FBCOM are as follows:
A clear advantage of DTM technology is better interoperability.
Other Systems and Devices
PRM can communicate with devices of HART, FF- H1, PROFIBUS, and devices that conform to the ISA100.11a standards. The communication can be performed through control systems such as CENTUM or STARDOM, or through Ethernet or HART multiplexers from field gateways that adopt DTM technology. This paper describes PRM architecture, with a focus on communication with field wireless devices using DTM, and handling of large scale networks.
Figure 2 System configuration of the new gateway
The latest YFGW410 Field Wireless Management Station (hereinafter referred to as new gateway) enables communication between host systems, such as PRM, and field wireless devices. The characteristics of the new gateway are as follows:
The system configuration in Figure 2 illustrates how the new gateway communicates with field wireless devices through YFGW510 Field Wireless Access Points. The new gateway provides two enhanced features over its predecessor (YFGW710), and these are used in managing PRM field wireless devices.
|Figure 3 New gateway with cache support|
When host systems such as PRM supports a large number of field wireless devices, problems in data acquisition occurs as the communication speed of wireless devices is slower than wired devices.
As a resolution for this issue, a memory cache was built into the new gateway during ISA100.11a gateway development. The cache can be configured using the Field Wireless Management Console (refer to Figure 2). With the cache, the new gateway can periodically acquire the self-diagnostic status of some or all of the 500 connected devices, and store the values locally so that they are readily available to any host system when requested. There is also a cache expiry policy to define when to automatically refresh data that is older than a specified time range.
When PRM requests for data, the new gateway will determine the validity of the data. If the data is new, the new gateway will send the data from the cache, if the data is old or not cached, it will acquire the corresponding data immediately from the devices. This design improves performance with minimal impact to existing systems. Figure 3 shows a comparison of the new and legacy gateways, with and without cache support.
On-demand communication is not very efficient for field wireless devices. Therefore as shown in Figure 3, communication performance can be improved by avoiding such communications. In addition, by utilizing the cache, the on-demand communication bandwidth can be preserved for other purposes. Field wireless devices can also reduce battery consumption since they do not need to respond to on-demand requests.
With the intelligence of current field digital devices, one main function such devices offer is the self-diagnosis function, which provides diagnosis alarms or self-diagnosis status. PRM depends on this data for its own device health monitoring logic. As the required device diagnosis parameter is automatically cached by the new gateway, users only need to select the candidate devices for self-diagnosis based on their criticality level.
Even though the new gateway is designed in such a way that only minimal changes are required in host systems, there was a need to enhance certain designs in PRM systems in order to fully maximize the new gateway features, as described below.
In the current design, PRM Client is responsible for using the Plug & Play function to register devices online through the FBCOM. FBCOM automatically performs DTM communication for hardware that only supports DTM communication (e.g. PROFIBUS and field wireless devices). This communication is enabled by the custom network topology configured by users during PRM engineering.
The device registration data (including communication capabilities) is then stored in the PRM database, which will then be used by the PRM server data acquisition engine.
PRM Client has now been updated to acquire and store information about the new gateway. Devices connected to the new gateway can utilize the cache, and the scheduling of data acquisition by PRM Server can be altered to cater to this enhancement.
|Figure 4 Device status display on all levels|
One of the main purposes of the PRM Server is device status monitoring. PRM Server uses a scheduler to periodically acquire device status information, and use an internal status decision engine to organize the information into different color codes. The various views in PRM Client will display the color coded information on all hierarchy levels. This enables users to quickly identify faulty devices. Figure 4 shows the field wireless device hierarchy in the Network view of PRM Client. Notice that the faulty device status is displayed on all parent nodes.
Depending on the number of devices connected, the scheduler can scan device statuses at intervals of 10 minutes to 24 hours. With the additional information (such as cache support) recorded during device registration, the scheduler can reduce the turnaround time of data acquisition for each device connected to the new gateway. In this way, the current scan specifications can be maintained even if the number of devices connected to the new gateway increase by tenfold.
Field Communication Server
As FBCOM supports DTM technology, minimal design changes were required to support ISA100.11a communication. The enhancements are as follows:
FBCOM has also been enhanced to support the WirelessHART™ gateways. This support is realized in the same manner as for ISA100.11a gateways, using DTM technology.
This paper has given a brief overview of the various PRM systems, and the roles they play in realizing the functions for managing and communicating with HART, FF-H1, PROFIBUS, and field wireless devices. The functions were implemented using FDT/DTM technology. This enables prompt support of new hardware (Yokogawa or third-party devices) as long as the required DTMs are made available. As FDT/DTM technology matures, it will form the basis for such new hardware support in the future too.
Plant Resource Manager (PRM) is a key platform for the Yokogawa VigilantPlant Asset Excellence initiative which aims to improve operations and maintenance and maximize the reliability and availability of plant assets by achieving greater predictability.
YFGW510 Field Wireless Access Point is based on wireless communications standard ISA100.11a for industrial automation of International Society of Automation (ISA). This product has backbone router function based on ISA, and combining this with Field Wireless Management Station (YFGW410) and/or Field Wireless Media Converter (YFGW610) composes the field wireless system.
YFGW710 Field Wireless Integrated Gateway comply to the wireless communications standard ISA100.11a for industrial automation of International Society of Automation (ISA), and relays ISA100 Device data to the system via integrated backbone router. Single unit of YFGW710 has integrated functions of backbone router, system manager, security manage, and gateway.