KOMIYA Hiroyoshi1 TAKIZAWA Hiroyuki1 MATSUKAWA Hideo1 KOZAKAI Kiyotaka1
In the course of developing CENTUM CS3000 R3 Revision 3.04, we also developed a new FFCS field control station which has achieved compact size and high reliability. The processor cards, being compact yet high performance, utilize field-proven "Pair & Spare" technology deployed in large-scale control systems, resulting in the implementation of sophisticated control functions and high reliability equivalent to the existing controllers designed for large-scale control systems. The FFCS is designed to be the same overall size as the existing "uXL" control unit, which enables easy replacement of the control unit without any changes. Moreover, CPU nodes, processor modules, ESB coupler modules, and V- net coupler modules have been newly developed for the FFCS. Especially, SEN bus (Serial Exchange Nest bus), which is a high-speed serial bus designed to suit the program copy and data equalization between dual redundant processor modules, has been developed as a new technology for data communication.
- Industrial Automation Systems Business Division
|Figure 1 External View of FFCS CPU Node|
Yokogawa Electric has been using Pair & Spare method as a reliability-enhancing technology for its line of distributed control systems (DCS) since the release of the CENTUM CS in 1993. As a result, the system has achieved an availability factor of seven 9's (99.99999%) for the record of operation to date. Under the basic concept "continually adopt new functions with assured function continuity", the CENTUM CS3000 R3 is being constantly improved through ongoing development and by introducing the latest technologies. Also strictly adhering to this basic stance for CENTUM CS R3 Revision 3.04, we have developed the FFCS compact field control station (Figure 1), which provides both the advanced control functions and high reliability levels required for DCSs, for use with small- to medium-scale systems. This article introduces the FFCS.
Figure 2 System Configuration
Figure 2 shows the configuration of the CENTUM CS R3 system. As for field control stations (FCS) to be connected to field devices to control the plant, we have added the small-size FCS (compact type, hereinafter called FFCS) featuring both high mountability and high distributability to the existing line of FCSs — standard, expandable and renewable FCSs that realize high mountability, and the highly distributable FCS that is suited for distributed topologies, according to the application capacity and the purpose of use.
FEATURES OF FFCS
|Figure 3 Conventional and
New Control Units
Figure 3 illustrates the external views of the conventional field control unit (FCU) and the field control unit (CPU node) of the FFCS and the features of the FFCS are described below.
- Compact and Expandable
Positive adoption of the latest technologies has made the FFCS as compact as only one-fifth the volume of the conventional control unit. The number of I/O nodes can be increased up to three. Thus the system can be expanded without increasing the number of CPU nodes.
- Advanced Functionality and High Reliability
The processor module employs Pair & Spare method, which is field-proven for controllers for large-scale systems, to switch the control right in case of system failure without any momentary shutdowns, thus minimizing the influence inflicted upon the process. While being compact, the module has the same advanced control functions and highly reliable architecture as those of controllers for large-scale systems. In addition, the processor module can be made completely dual- redundant.
- Migration from Existing uXL Systems
The external dimensions of the FFCS are the same as those of the control unit section of an existing uXL control system for small- to medium-scale plants. It is therefore possible to migrate to the FFCS by simply replacing the control unit section with the station. This feature enables the user to reuse its existing assets to the maximum possible degree and update the existing system with the minimum investment in the plant and equipment.
HARDWARE CONFIGURATION OF FFCS
|Figure 4 Configuration of Dual-redundant FFCS|
As shown in the dual-redundant configuration diagram of Figure 4, the processor module, power unit, communication bus, and I/O module of the FFCS can all be duplexed. The I/O module (IOM) and the field network I/O module (FIO) of CENTUM CS R3 have been made common to each other. This section focuses on the hardware of the newly developed CPU node.
A maximum of eight IOMs can be installed in the CPU node, allowing the CPU node to operate alone as the minimum system of the FFCS.
A maximum of three extension nodes (direct-coupling and remote nodes) can be connected to the CPU node. When connecting the CPU node and direct-coupling node, an ESB bus coupler module (EC401) is installed in the IOM section of the CPU node and an ESB bus slave interface module (SB401) is installed in the extension node. When using the remote node in place of the extension node, an ER bus master interface module (EB401) is installed in the IOM section of the CPU node or direct- coupling node.
Processor Module (CP401)
Figure 5 shows the dual-redundant configuration of the processor modules. The dual-redundant processor modules employ the field-proven Pair & Spare method. Each processor module comprises two MPUs, where the MPUs perform the same control computations and the computation results are cross- checked by the collators to detect transient errors. With the dual redundancy of processor modules, the transfer of the control right in case of system failure and the continuation of control are accomplished without any momentary shutdown, achieving high degrees of system availability.
Figure 6 shows the external view of the processor module. The module has been changed in shape from the conventional card-like form to a modular form in which the internal assembly is encapsulated in a molded housing. For the internal hardware configuration, we reused the hardware assets, i.e., the processor card (CP345) and SB bus interface card (SB301) of the industry- proven CENTUM CS3000, and incorporated them into a single module, while maintaining the software compatibility as much as possible. Equipped with the microprocessor which is field-proven as has been used for the industry-proven CP345 processor card, the processor module makes it possible to build scalable systems by using the same system software for small- to medium-scale plants and large-scale plants as well.
|Figure 5 Configuration of Dual-redundant
CP401 Processor Modules
In order to mount the CP345 and SB301 on a single module (i.e., to achieve downsizing), we actively adopted a programmable device in a fine-pitched multi-pin ball grid array (BGA) as a large- scale integration component, chip capacitors and resistors of 1005 size as small-size components, and new elemental technologies, including build-up boards for densely mounting such components.
The processor module contains a battery pack in order to back up the main memory in case of power failure. However, taking environmental protection into consideration, the conventional nickel-cadmium batteries have been abandoned and replaced with nickel-hydrogen batteries.
We have also developed the SEN bus for program copying and data equalization between the processor modules. Table 1 shows the specifications of the SEN bus in brief.
|Figure 6 External View of
CP401 Processor Module
Traditionally, data exchange between the processor modules has been performed using a parallel transmission method. In the case of the SEN bus however, the method has been replaced with the point-to-point high-speed serial transmission method to reduce the mounting area and the number of signal lines to one- tenth those of the conventional bus. Since the LVDS (EIA/TIA- 644 standard) method featuring small signal amplitudes has been adopted for the bus signal levels, radiation noise has been reduced and power consumption has also been dramatically reduced. From the point of view of high reliability, we added an error- detecting code and made it possible to connect/disconnect the module with the line electrified. The SEN bus is provided with error-detecting functions, such as constantly performing self- diagnoses using idle frames even in the absence of bus access requests. From a software point of view, the SEN bus inherits exactly the same interface as that of the existing backplane bus. Thus the FFCS features a design in which users need not be conscious of the SEN bus.
ESB Bus Coupler Module (EC401)
We have also developed the ESB bus coupler module (EC401) designed to connect the direct-coupling node to the CPU node. The module has one port for the ESB bus to communicate with the ESB bus interface module (SB401). By installing two units of the module, it is possible to support for the dual redundancy of the ESB bus.
V-net Coupler Unit
The FFCS employs the field-proven V-net as the control bus. The V-net coupler unit is equipped with a V-net data link control section and physical layer interface to provide signal isolation and level conversion for the V-net.
Yokogawa Electric's DCSs have evolved through the positive adoption of new technologies in line with market requirements (performance, functionality, and capacity increase). We have increased the capacity and functionality of FCSs' control units in harmony with improvements in semiconductor integration technology and enhancements in microprocessor performance. Since the amount of data for equalization between the dual- redundant processors has increased significantly, the conventional transfer capacity will no longer suffice.
We have retrofitted the backplane bus which has not been changed since the release of the CENTUM CS. In addition, we have developed the SEN bus (high-speed serial bus) for data equalization between the dual-redundant processor modules of the FFCS. The technical progress of the SEN bus holds promise for the bus to become even faster in future. Consequently, it will become possible to further enhance the functionality and performance of FCSs.
- Matsuda Toshihiko, Sano Hideo, Soggo Sadatoshi, Hazama Meguru, "Fault Tolerant Design for Field Control Stations", Yokogawa Technical Report , Vol. 18, 1994, pp. 10-13
- Komiya Hiroyoshi, Akai Hajime, Matsuda Toshihiko, Nishida Jun, "Fault Tolerance of Distributed Process Control Systems", The Institute of Electronics—Information and Communication Engineers Technical Research Report, Vol. 97, No. 98, 1997, pp. 35-40 (in Japanese)
- Kato Eiji, Nakamoto Eiji, Matsuda Toshihiko, "Features of Field Control Station Hardware", Yokogawa Technical Report, No. 26, 1999, pp. 6-9
- CENTUM and uXL are registered trademarks of Yokogawa Electric Corporation. The names of companies and products that appear in this document are the trademarks or registered trademarks of the respective holders.
바이오매스는 최근 화력 발전소가 이산화탄소 배출량을 줄일 수 있는 재생 가능 에너지원이기 때문에 점점 더 이슈가 되고 있습니다. Yokogawa 시스템은 바이오매스를 사용하는 발전소를 포함하여 모든 유형의 발전소에서 전 세계적으로 사용되고 있습니다. Yokogawa의 측정 및 제어 기술을 통해 발전소는 보다 효율적으로 운전이 가능하며 탄소배출을 줄일 수 있습니다.
석유 화학 제품, 무기물 또는 중간체를 생산하든 관계없이 화학 회사는 안전하고 호환되는 작업을 유지하면서 적시에 효율적인 방법으로 제품을 제공하는 비용과 마진 압박에 시달리고 있습니다. 또한 화학 회사들은 공급 원료 및 에너지 가격의 변동에 적응하고 가장 수익성 높은 제품 혼합을 시장에 제공해야 합니다.
Yokogawa는 벌크 화학 시장의 자동화 요구 사항을 세계적으로 지원해 왔으며 이 시장에서 인정받는 선두 주자입니다. Yokogawa는 제품, 솔루션 및 업계 전문 기술을 통해 시장 및 생산 요구 사항을 이해하고 플랜트의 수명주기를 통해 안정적이고 비용 효율적인 솔루션을 제공하기 위해 협력합니다.
1970년대 중반, Yokogawa는 EBS 전기 제어 시스템 (EBS Electric Control System)의 출시와 함께 전력 사업에 진출했습니다. 그 이후로 Yokogawa는 전 세계 고객에게 최상의 서비스와 솔루션을 제공하기 위한 기술과 역량의 개발을 꾸준히 지속해 왔습니다.
Yokogawa는 역동적인 글로벌 전력 시장에서 더욱 적극적인 역할을 수행하기 위해 글로벌 전력 솔루션 네트워크를 운영했습니다. 이로 인해 Yokogawa 내에서 보다 긴밀한 팀워크가 가능해져서 글로벌 리소스와 업계 노하우를 하나로 모았습니다. Yokogawa의 전력 산업 전문가들은 각 고객에게 정교한 요구 사항에 가장 적합한 솔루션을 제공하기 위해 협력합니다.
정수 및 하수 처리
Yokogawa는 보다 효율적인 사회를 만들기 위하여 에너지 최적화 기술 개발, 온실가스 감축, 오염 물질로부터 환경을 보호하는 견고한 제품 제작 등을 통해 지속 가능한 수자원 생산을 위한 제어 솔루션을 제공하고 있습니다. Yokogawa의 첨단 기술과 폭넓은 애플리케이션 노하우를 통해 고객과 협력하여 사업을 활성화하고 플랜트 수명주기 전반에 걸쳐 높은 가치를 제공할 수 있는 지속 가능한 솔루션을 제공합니다. 당사의 기술과 제품은 플랜트의 성능을 향상시키고 오늘날의 수자원 시장에서 경쟁적으로 운영할 수 있도록 보장하며 운영비를 절감합니다. Yokogawa는 지자체 및 공업용수 처리 시장에서 광범위한 수처리 응용 분야를 지원합니다.
지열에너지는 기상 조건에 의존하지 않기 때문에 일 년 내내 안정적인 전력을 공급할 수 있습니다. 또한 어떤 연료도 지상에서 태우지 않으며 매우 적은 양의 이산화탄소만 배출되므로 환경친화적입니다. 태평양, 일본, 필리핀, 인도네시아, 뉴질랜드, 멕시코, 코스타리카, 미국 등의 국가에서 태평양 연안 벨트 ("불의 고리"라고도 함)를 따라 풍부한 지열 자원이 있습니다. 다른 지열 활동 지역에 위치한 아이슬란드, 터키 및 이탈리아와 같은 국가들과 협력합니다. Yokogawa는 현재까지 일본, 동남아시아 및 기타 지역의 30개 지열발전 프로젝트를 실행한 경험을 바탕으로 지열발전 시스템의 신뢰성 및 유지 관리 효율성을 향상시키는 다양한 측정 및 제어 기술을 제공하고 있습니다.