Yokogawa has implemented in the CENTUM CS 3000 R3 a new, two-layer I/O architecture that integrates field networks into a distributed control system with general analog and digital inputs/outputs. This new architecture consists of two types of nodes: one directly connected to a controller CPU and capable of communicating and updating a large amount of data at a high speed, and the other connected to a controller CPU via a communication bus and placed near field devices. These two types of nodes allow flexible system configuration according to the applications while assuring a sufficiently short data updating period and reducing of wiring costs.
- Industrial Automation Systems Business Div.
The recent increase of devices enabled for a field network such as the FOUNDATION™ Fieldbus is phenomenal. This has been amplifying a requirement for distributed control systems (DCSs) to be capable of constituting a more pliant and efficient production control system by means of flexible connections to field networks in addition to traditional 4 to 20 mA signals1. In response to this, Yokogawa has developed a new I/O architecture that allows existing I/O devices and field networks to be flexibly integrated under a CENTUM CS 3000 R3. This paper describes the requirements for integrating field networks into a CENTUM CS 3000 R3, and then introduces an example.
REQUIREMENTS FOR I/O SYSTEMS FOR A DCS
Figure 1 I/O System for CENTUM CS 3000 R3
An I/O system for a DCS is usually installed in the cabinet of a field control station (FCS) that carries out process control functions2. Figure 1 illustrates the positioning of an FCS in a CENTUM CS 3000 R3 system and outlines the I/O system.
The requirements for FCS's I/O system to integrate field networks and the existing I/O include:
- Appropriate integration of field networks with no influence on the control functions
- Appropriately short data updating periods, including the data of existing I/O
- Reduced initial costs, especially wiring costs
Field Network Integration into DCS
Acquiring data via communication generally requires the use of a communication protocol, and integrating a field network is no exception. In particular, when connecting a field network to a DCS, it needs to be taken into account that the execution of a complex protocol may not largely affect the usual inputs or outputs, or control actions. Further, in the case of recently used, high-speed field network such as Profibus-DP is used, the DCS needs to be able to acquire a large amount of data within a short time for effective use of its merits. Hence, when separating a module that performs communications and a module that carries out controls, a sufficiently wide band should be provided for data exchange between those modules.
Data Update Periods
For both the inputs/outputs via field networks and usual analog and digital inputs/outputs, the I/O data needs to be updated at periods suitable for the respective applications. Namely, the data of those inputs and outputs for which high-speed control is required need to be updated at short periods, while, for those inputs whose data need not be updated at short periods but that are many in number, such as monitoring points, an update period that may not influence the execution of controls is sufficient. It is typical that these different types of inputs/outputs exist for a control object and thus each controller of a DCS is required to perform I/O data updates at different periods without affecting each other. Of course, also when connecting field networks, the update periods of the other data must be prevented from being influenced to the utmost.
Reduction of Field Wiring Costs
It is well known that the costs for field wiring are not a small part of the overall costs when employing a plant control system, and thus when considering the I/O system for a DCS, the deliberate reduction of field wiring costs is an inevitable aim.
Where diverse field networks and traditional analog and digital inputs/outputs co-exist, the I/O system for a DCS is required to have the capability of accommodating flexible field wiring schemes in accordance with the physical plots of plant equipment and plant characteristics.
Integration with CENTUM CS 3000 R3
Figure 2 Two-layer I/O System
The CENTUM CS 3000 R3 meets the aforesaid three requirements by adopting the I/O system architecture in which, in addition to I/O modules directly connected to a controller, remotely installed I/O modules can be connected to the same controller as illustrated in Figure 2. The following details this architecture.
Two-layer I/O System
To make the CENTUM CS 3000 R3 meet the aforementioned requirements, the two-layer I/O system was developed. In particular:
- The fast bus running across the backboard of a node in which I/O modules are to be installed, was expanded to a controller to "directly" connect I/O modules via a fast bus. Nodes of this type are referred to as local nodes. The internal bus used here allows for transmissions at 128 Mbps, so the CPU in a controller can access I/O modules in a local node at an equally high speed as when accessing the local processor itself.
- Data acquisition and transmission from/to remotely installed I/O nodes are enabled by installing a remote I/O bus module in a local node. These remotely installed nodes are called remote nodes. The remote I/O bus adopts 10-Mbps Ethernet and can be physically extended with general-purpose Ethernet devices. That is to say, nodes can be distributed in a wide area using wireless communication, the public communication network, and the like.
- For communication with remote nodes, a communication module is also installed in each remote node and communication protocols are deliberately installed such that both the I/O points requiring high-speed communication of a little amount of data and the points requiring a not-so-fast communication of a large number of data can be assigned to the same node.
To facilitate integration of field networks, the following are also achieved in this architecture:
- The field network protocols are executed inside the respective communication modules to prevent an increase of the load on the controller's CPU.
- The settings for each field network, such as the data items to be acquired, can be made using the fill-in-form method for ease of engineering.
Features and Benefits
Next, the features and benefits of the new architecture are explained in comparison to the conventional architecture.
Reduction of the wiring costs by remote bus had already been realized before this new I/O architecture; however, connecting to a high-speed, large-capacity field network has encountered the problem that the communication band of the remote bus meant that the field network's merits could not be used optimally. Conversely, using only nodes connected directly to a CPU inevitably lengthened the field wiring cables, resulting in increased wiring costs. Now, these problems have been cleared by our new I/O system architecture, since it uses the remote bus and direct connections in the same controller to allow the method suitable for each application to be chosen flexibly.
The actual benefits include the following:
- Fast I/O data update periods can be achieved for control objects requiring high-speed control by installing the corresponding I/O modules in a local node.
- For control objects that do not require fast I/O data update periods, field wiring costs can be reduced by distributing remote nodes that contain I/O modules in the field.
- Benefits of a high-speed field network such as Ethernet and Profibus-DP can be enjoyed fully by installing the corresponding communication module in a local node to provide a sufficiently wide band for communication between the controller's CPU and communication module.
- Communication modules for which updates of a large amount of data is required though at not-so-fast periods, such as a module for the FOUNDATION™ Fieldbus communication, can be installed either in a remote node or in a directly connected mode, helping reduce field wiring costs.
Adoption of the architecture described in this paper has allowed us to provide an I/O system that meets all of the requirements listed at the beginning:
- appropriate integration of field networks with no influence on the control functions;
- appropriately short data updating periods, including the data of existing I/O; and
- slashed initial costs, especially wiring costs.
We believe that the new architecture can cope with ever- diversified field networks emerging in the near future since it accommodates flexible configurations such as a broad band secured for communication between a controller's CPU and a field network communication module.
Field networks will surely be further developed, and are ever- becoming more important in the field. We believe that our I/O system architecture is capable of meeting the various requirements of the times. From now on, we would like to continuously satisfy user needs by keeping our eyes on field network trends and developing new field network modules for our DCSs.
- Mori Hiroshi, "CENTUM CS Fieldbus Communication Functions," Yokogawa Technical Report, No. 27, 1999, pp.17-40
- Oda Shinji, "Control Functions of CENTUM CS 3000," Yokogawa Technical Report, No. 29, 2000, pp. 15-18
- All product and company names appearing in this paper are trademarks or registered trademarks of their respective holders.
바이오매스는 최근 화력 발전소가 이산화탄소 배출량을 줄일 수 있는 재생 가능 에너지원이기 때문에 점점 더 이슈가 되고 있습니다. Yokogawa 시스템은 바이오매스를 사용하는 발전소를 포함하여 모든 유형의 발전소에서 전 세계적으로 사용되고 있습니다. Yokogawa의 측정 및 제어 기술을 통해 발전소는 보다 효율적으로 운전이 가능하며 탄소배출을 줄일 수 있습니다.
석유 화학 제품, 무기물 또는 중간체를 생산하든 관계없이 화학 회사는 안전하고 호환되는 작업을 유지하면서 적시에 효율적인 방법으로 제품을 제공하는 비용과 마진 압박에 시달리고 있습니다. 또한 화학 회사들은 공급 원료 및 에너지 가격의 변동에 적응하고 가장 수익성 높은 제품 혼합을 시장에 제공해야 합니다.
Yokogawa는 벌크 화학 시장의 자동화 요구 사항을 세계적으로 지원해 왔으며 이 시장에서 인정받는 선두 주자입니다. Yokogawa는 제품, 솔루션 및 업계 전문 기술을 통해 시장 및 생산 요구 사항을 이해하고 플랜트의 수명주기를 통해 안정적이고 비용 효율적인 솔루션을 제공하기 위해 협력합니다.
1970년대 중반, Yokogawa는 EBS 전기 제어 시스템 (EBS Electric Control System)의 출시와 함께 전력 사업에 진출했습니다. 그 이후로 Yokogawa는 전 세계 고객에게 최상의 서비스와 솔루션을 제공하기 위한 기술과 역량의 개발을 꾸준히 지속해 왔습니다.
Yokogawa는 역동적인 글로벌 전력 시장에서 더욱 적극적인 역할을 수행하기 위해 글로벌 전력 솔루션 네트워크를 운영했습니다. 이로 인해 Yokogawa 내에서 보다 긴밀한 팀워크가 가능해져서 글로벌 리소스와 업계 노하우를 하나로 모았습니다. Yokogawa의 전력 산업 전문가들은 각 고객에게 정교한 요구 사항에 가장 적합한 솔루션을 제공하기 위해 협력합니다.
정수 및 하수 처리
Yokogawa는 보다 효율적인 사회를 만들기 위하여 에너지 최적화 기술 개발, 온실가스 감축, 오염 물질로부터 환경을 보호하는 견고한 제품 제작 등을 통해 지속 가능한 수자원 생산을 위한 제어 솔루션을 제공하고 있습니다. Yokogawa의 첨단 기술과 폭넓은 애플리케이션 노하우를 통해 고객과 협력하여 사업을 활성화하고 플랜트 수명주기 전반에 걸쳐 높은 가치를 제공할 수 있는 지속 가능한 솔루션을 제공합니다. 당사의 기술과 제품은 플랜트의 성능을 향상시키고 오늘날의 수자원 시장에서 경쟁적으로 운영할 수 있도록 보장하며 운영비를 절감합니다. Yokogawa는 지자체 및 공업용수 처리 시장에서 광범위한 수처리 응용 분야를 지원합니다.
지열에너지는 기상 조건에 의존하지 않기 때문에 일 년 내내 안정적인 전력을 공급할 수 있습니다. 또한 어떤 연료도 지상에서 태우지 않으며 매우 적은 양의 이산화탄소만 배출되므로 환경친화적입니다. 태평양, 일본, 필리핀, 인도네시아, 뉴질랜드, 멕시코, 코스타리카, 미국 등의 국가에서 태평양 연안 벨트 ("불의 고리"라고도 함)를 따라 풍부한 지열 자원이 있습니다. 다른 지열 활동 지역에 위치한 아이슬란드, 터키 및 이탈리아와 같은 국가들과 협력합니다. Yokogawa는 현재까지 일본, 동남아시아 및 기타 지역의 30개 지열발전 프로젝트를 실행한 경험을 바탕으로 지열발전 시스템의 신뢰성 및 유지 관리 효율성을 향상시키는 다양한 측정 및 제어 기술을 제공하고 있습니다.