고성능 온도 전송기 YTA510은 써모커플(열전대), RTD, 옴 또는 DC mV 입력을 받아 들입니다. 이 전송기는 무선 신호를 사용하여 프로세스 변수 뿐만 아니라 설정 Parameter도 전송합니다. 전송기는 내부 배터리로 작동하며 하드 와이어 링이 필요하지 않으므로 설치 비용이 감소 될 수 있습니다. 통신은 ISA100.11a 프로토콜 스펙을 기반으로 합니다. 분리형 Antenna 모델은 확장 케이블을 사용하여 고 이득 안테나*1과 함께 사용할 수 있습니다. 초 저 전류 소비 설계로 긴 수명 배터리로 수 년간 무선 작동이 가능합니다.
|Wireless Specifications||Communication protocol||ISA100.11a / IEEE802.15.4|
|Data rate||250 kbps|
|Frequency||2.400 - 2.4835 GHz license free ISM band|
|Radio security||AES 128 bit codified|
|RF Transmitter power||Max. 11.6 dBm (fixed)|
|Antenna||+2 dBi Omni directional
Detachable Antenna type model (Amplifier housing code 8 or 9) can be used with a high-gain antenna1 with an extension cable.
|Standard Specifications||Variety of sensor inputs||Single input: Amplifier housing code 7
Dual input: Amplifier housing code 8or9
RTD: Pt100 & Pt200 & Pt500 (IEC) and ohms
Thermocouples (T/C): B, E, J, K, N, R, S, T(IEC) and DC m volts (-10 to 110 mV)
Input type is selectable: Thermocouples, 2-,3-, and 4-Wire RTDs, ohms and DC milivolts.
4-Wire is available for Sensor 1 input.
|A/D accuracy||Pt100: ±0.3°C
Type k: ±1°C
|CJC accuracy (T/C only)||±0.5°C|
|Update period||1 sec to 60 min selectable|
|Battery life||Typical battery life is 10 years at 10 seconds update time or 8 years at 5 seconds update time in the following conditions.2
Detachable Antenna type model (Amplifier housing code 8 or 9)
low power mode
Ambient temperature: 23±2°C
Device role: IO mode
LCD display: off
|Physical Specifications||Antenna||+2 dBi Omni directional monopole type|
|Weight||2.8kg（Without battery pack and mounting bracket）|
|Power supply||Lithium thionyl chloride batteries (size D×2)|
|Battery Replacing||Included zone 0|
|Certification||Explosion protected type||ATEX, FM, CSA, IECEx Intrinsically safe Approval|
|EMC Conformity Standards||EN61326-1 Class A, Table 2 (For use in industrial locations), EN61326-2-3|
|R&TTE Conformity Standards||ETSI EN 300 328, ETSI EN 301 489-1,
ETSI EN 301 489-17, EN61010-1, EN61010-2-030, EN62311
|Regulation Conformity of the Wireless Module||• FCC Approval
• IC Approval
|Safety Requirement Standards||EN61010-1, EN61010-2-030|
|Others||Ambient temperature||-40 to 85°C|
- Subject to the Radio law regulation of each country.
- Environmental condition such as vibration may affect the battery life.
- As the main automation contractor (MAC) for this plant construction project, Yokogawa Brazil engineered, installed, and commissioned an integrated control and instrumentation solution
- Yokogawa Brazil completed the commissioning of these systems ahead of schedule and the production of green polymer was started just one week later
Eliminating the wire using wireless transmitter is the perfect solution for rotating equipment. It establishes data collection between the transmitter and the gateway by reliable communication even though the dryer was rotating.
Caustic soda and hydrochloric acid, produced in electrolyzer plants, are fundamental materials used in varieties of industries; chemicals, pharmaceuticals, petrol-chemicals, pulp and papers, etc. Profit is the result of the effective production with minimized running / maintenance cost. Proper control of the process brings you stabilized quality of products with the vast operational profit.
- The distance is not so long, but there are many pipes and tanks ("Pipe Jungle") in the field.
- Had to avoid the obstacles and take care multi path condition.
Repeater is installed on high place between control room and monitor position. The extend cable is used for antenna of Gateway.
- Temperature Transmitter (YTA) x1, Pressure Transmitter (EJX) x2
Continuous technology improvement is ongoing in the pulp & paper industry to obtain the best possible performance. The improved plant performance translates to the higher quality improvement and lower cost, and simultaneously environmental friendly plant operation.
- Manual temperature reading requires walking about 130 m and climbing up and down elevated sections of the dryer stages.
- Multiple temperature measurement points along the various stages of the dryer require many cables to the control room.
- Very high humidity.
- Wireless temperature measurement
gateway x1, transmitter (YTA) x1
repeater x1: between gateway and YTA.
- High quality wireless communication was confirmed.
With repeater at center: The packet error rate was 0%.
Delayed Coker is a type of coker who's process consists of heating residual oil feed to its thermal cracking temperature in a furnace. The most important variable in industrial furnace control is temperature. Temperature is measured throughout the furnace in different zones and temperature effects the materials being manufactured and therefore must be precisely monitored to prevent deviations in quality of the final product.
Blending plays a key role in industries such as food, healthcare and chemicals etc. Temperature and vacuum measurements are very important in minimizing the moisture content to ensure the quality of the final product. Strictly maintaining them throughout the process ensures the final product yield.
Geothermal power plants create electricity from geothermal energy. These power plants are similar to other steam turbine station; however their heat source is that of the earth's core. The created steam is used to turn the turbine for the production of electricity. Technologies include Dry steam, Flash steam and Binary cycle power stations with Binary cycle being the most common geothermal plant in current production. In the process of geothermal power generation the facility needs to monitor various processes, as in this case steam line pressure sits in remote from control room's location.
A horizontal rotary miller used to grind the limestone rocks with metallic balls as grinding stones. This is used as the raw ingredient to produce cement powder. The temperature needs to be monitored in order to control the process and the quality of the final product. The user was using an induction temperature measurement based on a rail system that was very fragile and therefore unreliable.
Direct Reduction Iron (DRI) is one of the processes to reduce oxygen from iron oxide pellets for steel plant. More than 90% of DRI processes use heated LNG as process gas where PID control for temperature or interlock control is of vital importance.
One important risk to manage with regard to coal stacks is preventing fires due to spontaneous combustion.
In recent years, more field wireless devices have been used in hazardous areas. Meanwhile, in plants that are usually recognized as hazardous areas, there are numerous metallic tanks and pipes that easily shield or reflect radio waves, as discussed later, thus resulting in a poor environment for wireless communication.
The innovation of wireless technology increases the use of wireless communication in the industry. The introduction of wireless communication to plants, however, requires strict features such as robustness, real-time responsiveness, and low power consumption. This has restricted the use of wireless communication to limited applications such as data logging and device status monitoring that does not require strict real-time responsiveness and data arrival reliability in communication.
기술 및 솔루션, 요꼬가와에 대한 자세한 정보를 찾고 계십니까?견적 및 기술문의